|Place of Origin:||P. R. China|
|Model Number:||Customized product|
|Minimum Order Quantity:||1 pcs.|
|Price:||Customized Product, Quoted Case By Case|
|Packaging Details:||Seaworthy packing|
|Delivery Time:||6～8 months|
|Payment Terms:||L/C, T/T|
|Material:||Carbon Steel, Stainless Steel||Driving Energy:||LP Steam, Fuel Oil Or Gas, High Temperature Flue Gas Above 250℃|
|Application:||Recovery Of Low Grade Heat||Advantage:||Little Energy Input, High COP|
|Warranty Period:||12 Months Since Operation Or 18 Months Since Delivery|
Absorption Heat Pump / absorption heat transformer to obtain high temperature heat source requiring little energy input
The absorption heat transformer (AHT) intends to obtain high temperature heat source and is applicable for petrochemical, coal chemical, inorganic chemical, rubber, polysilicon and other industries generating waste heat or requiring heat supply. Taking excess low grade waste heat from the original process system which is unable to be used directly as the medium temperature driving heat source, AHT requires no external driving heat source. With the absorption circulation technology of the unit itself, AHT can produce high temperature heat source with a temperature apparently higher than that of the low grade waste heat, which then can supply heat to the original process system or other consumers. Besides recovering the industrial waste heat, AHT also produces higher grade heat source so as to “pump” energy from low grade heat source to a high grade one and thus substantially reduce the energy consumption. What’s more, the operation process of AHT requires little energy input, therefore, it can create excellent economic and environmental benefits in terms of energy conservation and emission control.
II Work principle
AHP uses LiBr/H2O as working fluid and is made up of high pressure end, low pressure end and solution heat exchanger, pump and valves in between. The high pressure end consists of a generator and a condenser arranged in a casing. The low pressure end consists of an evaporator and an absorber arranged in a casing. The working principle is shown in the diagram. Driven by the low grade waste heat, the generator at the high pressure end is heated and generates steam, which condenses into liquid water in the connecting condenser. The liquid water, pressurized at the refrigerant liquid delivery pump, flows into the evaporator at the high pressure end, where it is heated by the low temperature and generates HP steam. The HP steam in the absorber is absorbed by the concentrated solution from the generator, where high temperature absorption heat is generated. The absorption heat then heats the hot water in the heat transfer tube in the absorber and thus produces high temperature water. The solution heat exchanger is to fulfill the heat exchange when the lithium bromide solution circulates at the HP and LP end.
1) AHT recovers low grade industrial waste heat above 70℃ and produces hot water with 25～50℃ temperature increase or steam;
2) The capacity of single AHT unit is 500～10000kW;
3) The coefficient of performance is 0.45～0.49;
4) AHT requires little energy input for operation.